The EN 54 Fire detection and fire alarm systems is a mandatory standard of European Union market that specifies requirements and laboratory test for every component of fire detection and fire alarm system.
EN 54-16 Standard
Voice alarm control and indicating equipment
Immediate availability. It must be able to send warning message 10 seconds after applying electric power supply.
Immediate response. Less than 3 seconds after an alarm is set off.
Supervision of the critical signal route: the alarm system link, the PA system, the amplifiers and the loudspeaker lines. This supervision must not interfere with the normal operation of the system and must be supervised at least every 100 seconds.
Status indication and fault monitoring.
On some occasions a back-up amplifier is compulsory in case there is a problem with one of them.
Voice evacuation system all in one amplifier
Built-in 500W digital amplifier
Auto detection for system failure, speaker output, paging Mic, etc.
6 zones individual management
Zones extendable by extender amplifier
Support remote control via computer
Extendable to 120 zones
Comply with EN54-16 requirements